Results 1 to 4 of 4
04-15-2010, 03:26 PM #1
Should I be concerned about the white substance at this breaker, what causes it? It is a 60 amp breaker feeding a panel next to it (less than a foot away).
Similar Threads:Tom Rees / A Closer Look Home Inspection / Salt Lake City, Utah
04-15-2010, 04:19 PM #2
That appears to the filler (sometimes ceramic) that is installed over the adjustment screws at the factory.
04-15-2010, 04:46 PM #3
Re: BreakerIt Might have Choked Artie But it ain't gone'a choke Stymie! Our Gang " The Pooch " (1932)
Billy J. Stephens HI Service Memphis TN.
04-15-2010, 05:10 PM #4
Seems to be a common occurance of Gould/ITE, ITE Siemens breakers in a damp location. I would not get too worked up about it.