Results 1 to 2 of 2
Thread: Ground rod in slab
05-14-2010, 07:59 AM #1
Ground rod in slab
The ground cable from the service panel enters the slab a couple inches away from a grounding rod. I can not verify that the cable is actually attached to the rod.
I entered the ground as not inspected but was curious what others might say in addition to this.
Would you recommend a new ground to ensure that there actually is a proper connection?
In the photo, the black cable is for other equipment.
05-14-2010, 06:14 PM #2
Re: Ground rod in slab
A couple of quick observations:
- that is a pipe clamp, not a rod clamp
- the ground rod is (presumable) 8 feet long and is quite obviously therefore not 8 feet in the ground
- that black ground conductor to "other equipment" is likely all wrong