Results 1 to 2 of 2
Thread: Ground Wire
07-06-2007, 11:10 AM #1
07-06-2007, 11:21 AM #2
Re: Ground Wire
Are you sure its not a bonding jumper??
If it is a ground I believe its required to be attached to the supply within 5ft upon entering the structure.
Most of the time the bonding of the piping (water & gas) is done at the water heater.
Oh and as far as usting stranded Al, I am unsure. However, I dont see what could be a problem...
Last edited by Martin lehman; 07-06-2007 at 11:22 AM. Reason: forgot the original question..