Results 1 to 2 of 2
Thread: panel box next to window
07-12-2010, 06:44 PM #1
panel box next to window
Does anyone know of any requirement of a panel box, such as this, next to an openable window. I'm thinking it should have 3ft clearance....
I wasn't able to open this box to see exactly what was inside, however, I suspect it is related to an irrigation , sprinkler system....maybe the control panel?
07-12-2010, 06:56 PM #2
Re: panel box next to window
First, that is not a panel, that is a low voltage landscape lighting transformer, and it is plugged into the wrong kind of cover plate (needs a bubble type cover).
If it were a panel, it could still be in front of the window, just need to trim back/remove the bushes to provide the 30" wide by 36" deep working space.