Results 1 to 2 of 2
03-16-2011, 05:23 PM #1
Feeder cables, penetration through box
Is this an acceptabel installation for the feeders in this service disconnect box. There are 2 one hundred amp breakers. Single family home built in 1997.
03-17-2011, 11:12 AM #2
Re: Feeder cables, penetration through box
Those yellow fiitng look like bushing used in metal studs. They are not a listed connector for those cables. The cable needs to be secured to the enclosure.
All answers based on unamended National Electrical codes.