Results 1 to 3 of 3
12-13-2012, 09:37 AM #1
Tankless WH Receptacle Cover Plate
12-13-2012, 09:15 PM #2
Re: Tankless WH Receptacle Cover Plate
That receptacle outlet is required to be:
- listed and identified as weather-resistant (WR)
- listed and identified as tamper-resistant (TR)
- GFCI protected
- and if that enclosure is not a raintight enclosure, then the receptacle outlet also needs to have a bubble type cover for it (was there a door over that area, or was it open?)
That looks recessed into the wall, is the proper wall insulation R-value in the wall behind it?
That water heater is bottom fed, does it have an atmospheric vacuum breaker installed?
Is that cord rated for that use?
12-14-2012, 08:14 AM #3