Results 1 to 2 of 2
11-22-2008, 03:37 PM #1
Vent connection to Furnace Blower
Attic gas furnace, Goodman GMP075-3. Picture shows where it looks like the installer just set a piece of B-Vent over the exhaust fan outlet. Shouldn't there be an adapter to provide a tight fit? The second picture just shows the B-vent run through the roof deck. I think somebody got the fire stop requirement wrong.
Similar Threads:The above statements are expressed solely as my opinion and in all probability will conflict with someone else's.
Stu, Fredericksburg VA
11-23-2008, 11:22 AM #2
Re: Vent connection to Furnace Blower
It also looks like you have some water issues on the b-vent and the roof sheathing.