Results 1 to 1 of 1
08-06-2016, 08:24 PM #1
Fan Motor Changed - Now Wiring Sticking Out?
We had a local HVAC company, highly recommended on Yelp, come out to repair our central a/c not cooling down the house. First they replaced the capacitor, said the fan motor would last another 1-2 years. After, the a/c would not go above 76, something was definitely wrong.
They sent out a different guy who tinkered with the system for 3 hours and then tried to tell me that DTE was cutting back on our electricity during the day because it was so hot out. I told him that was straight up BS. He figured nothing out, except that it was the fan motor, the one that was supposed to last another 1-2 years according to the first tech the day before.
We had them come out a 3rd time to change out the fan motor, they charged us $82 for 2 of the 3 visits, even though this should have been able to be addressed in one visit. This guy left the wires sticking out of the top of the unit, on top of the fan grille. I have attached 4 photos. This seems like a very lazy job and not done properly by a certified and licensed HVAC technician. Was this done properly? Any small child or animal can come along and pull these out, not to mention it's Detroit and we get very harsh weather here. Thanks.