Results 1 to 5 of 5
05-05-2007, 02:19 PM #1
05-05-2007, 02:47 PM #2
The pump is considered the trap. I would recommend the lines be run separate for drain lines, I can not tell if the shut off is wired for the pump, so that it will turn the furnace and A/C off if the pump stops working if this is in a living space.
05-05-2007, 07:55 PM #3
I've never seen a condensate pump installed such that it meets the requirements of a trap.
There should be a trap between the AHU and the condensate pump.
05-06-2007, 12:05 PM #4
We always putt a trap before the condensate pump. that setup in the picture will stink up the house during the heating season. this is why you should put it there
05-06-2007, 12:11 PM #5